- Flower Bulb and Perennial Sales Position - Portland (Oregon) USA
- Plant Production Scientist - Brooklyn (NY) USA
- Greenhouse Assistant Grower - Abbotsford (B.C.) Canada
- Technical Sales Representative - South Western Ontario, Canada
- Farm Manager - West Africa
- Managing Agronomist - Surinam
- Vegetal Material Programme Leader - Cisterna di Latina (Latium), Italy
- Head of Sales North America - Sacramento (CA) USA
- Inkoop Specialist Holland Product - Netherlands
- Vegetable Grower - Australia
- Australia: Opportunity to comment on national tree standard revision (1)
- Schroll is developing the hydrangea production in Portugal (3)
- US: AFE educational grant applications due June 1 (2)
- "Plenty of opportunities to expand markets outside Russia's major cities" (1)
- Coloured by Gerbera presents new assortment (1)
- "Customers are looking for different shades of red roses" (1)
- US: Is the era of thermal transfer printers over? (2)
- India: Government gives 50% subsidy on a poly house (46)
- Southern hemisphere's largest solar water heating facility at LVG Plants (1)
- Photoreport: Horticontact (1)
Top 5 -yesterday
Top 5 -last month
Top 5 -last week
Impact of screen gaps above the central path
A Ventilation Jet system blows dry and cold air from the top compartment into the greenhouse to lower the greenhouse relative humidity (and temperature). By using a screen gap above the main path, the excess heat and humidity could escape. The efficacy of this system was investigated at a commercial greenhouse; the air flow through the VJ and through the screen gap as well as the horizontal temperature profile were measured in spring 2017.
The outcome was that less than 3% of the incoming air leaves the greenhouse through the screen gap above the central path; the vast majority of the air (> 97%) passes through the screens to the top compartment. It can be therefore concluded that the small gaps above the central path should not be applied in the specific greenhouse. Horizontal temperature difference (2.0 °C - 2.7 °C per 100 m) was recorded when both screens and supplementary lights were used. Closing the gap above the main path and replacing it with more and evenly spaced gaps with controllable size can probably homogenize the temperature distribution. This horizontal temperature difference did not occur when the supplementary lights were switched off.
The described study was part of “Kas als Energiebron” program, it took place at Gardener’s Pride greenhouse in Beetgum, NL and it was funded and performed in cooperation with LTO Glaskracht Nederland and the Dutch Ministry of Economic Affairs.
Source: Wageningen University & Research
Publication date :
Receive the daily newsletter in your email for free | Click here
Other news in this sector:
- 09/21/2018 ‘Generic light recipe per crop is bullshit’
- 09/18/2018 Japan: New plant species discovered in museum is probably extinct
- 09/17/2018 US (CT): Operating automated greenhouses in Cheshire
- 09/13/2018 LED Grower's Guide for Ornamentals
- 09/11/2018 Nutrient removal from drainwater: the e-Phos showcased
- 09/11/2018 UL/CSA certified cable welding system launched
- 09/11/2018 "No duplicate sensors, lower costs and uniform data"
- 09/10/2018 Smart cameras predict future development of cuttings
- 09/05/2018 New filters for Ball Seed WebTrack
- 08/29/2018 New LED toplighting with higher output for light-loving crops
- 08/29/2018 "Grower becoming more of an entrepreneur"
- 08/28/2018 Tunisia: Underground irrigation tech helps growers counter drought
- 08/28/2018 UK: New conference to drive technology advancements in horticulture
- 08/28/2018 How do LED grow lights work?
- 08/24/2018 Plants control photosynthesis similarly, regardless of origin
- 08/24/2018 New high intensity top-light launched
- 08/23/2018 Australia: What research should the nursery industry invest in?
- 08/23/2018 The label is (not) blowing in the wind
- 08/23/2018 UVC light also suitable to disinfect auction buckets or cultivation vases
- 08/22/2018 "Nine hectares is a big project, also by British standards"