Job offersmore »
- Horticultural Specialist - Emeryville (CA) USA
- Sales Manager Europe Division
- Grower - Delta, (OH) USA
- Export Sales - Perth, Australia
- Production Manager Indonesia - Magelang/Central Java, Indonesia
- Director ASIA Research Station Operations - Bangkok, Thailand
- Spécialiste Technique et commercial Biocontrôle pour l’Ouest de la France
- Technical sales Specialist North Europe - Benelux and Scandinavia
- Grower Manager - Tuakau, New Zealand
- Sales representative - (TN, KY, NC, SC and GA) USA
Last commentsmore »
- Women's Day: "Russian market is growing up" (158)
- Will sea freight be an alternative to Latin American air freight? (243)
- India: Government gives 50% subsidy on a poly house (1237)
- Grower tickled pink with Pink Kisses from Portugal (6)
- "Hydrangea market finally develops in a more quality oriented direction" (3)
- "25% annual production growth Mexican phalaenopsis" (35)
Top 5 - yesterday
- No news has been published yesterday.
Top 5 - last week
Top 5 - last month
Exchange ratesmore »
Impact of screen gaps above the central pathThe application of New Cultivation Techniques (in Dutch “Het Nieuwe Telen”) in Dutch greenhouses during the last years has resulted in energy savings. Instead of screen gaps, growers close their screen(s) completely and use a Ventilation Jet system to lower the greenhouse air relative humidity (and temperature) in a controllable way.
A Ventilation Jet system blows dry and cold air from the top compartment into the greenhouse to lower the greenhouse relative humidity (and temperature). By using a screen gap above the main path, the excess heat and humidity could escape. The efficacy of this system was investigated at a commercial greenhouse; the air flow through the VJ and through the screen gap as well as the horizontal temperature profile were measured in spring 2017.
The outcome was that less than 3% of the incoming air leaves the greenhouse through the screen gap above the central path; the vast majority of the air (> 97%) passes through the screens to the top compartment. It can be therefore concluded that the small gaps above the central path should not be applied in the specific greenhouse. Horizontal temperature difference (2.0 °C - 2.7 °C per 100 m) was recorded when both screens and supplementary lights were used. Closing the gap above the main path and replacing it with more and evenly spaced gaps with controllable size can probably homogenize the temperature distribution. This horizontal temperature difference did not occur when the supplementary lights were switched off.
The described study was part of “Kas als Energiebron” program, it took place at Gardener’s Pride greenhouse in Beetgum, NL and it was funded and performed in cooperation with LTO Glaskracht Nederland and the Dutch Ministry of Economic Affairs.
Source: Wageningen University & Research
Publication date: 11/14/2017
Other news in this sector:
Leave a comment: (max. 500 characters)
- All comments which are not related to the article contents will be removed.
- All comments with non-related commercial content, will be removed.
- All comments with offensive language, will be removed.