- Head Grower – High Technology Organic Greenhouse
- Import and Export Sales Manager
- Sales Manager - US
- Account Manager - Canada
- Grower | Cannabis
- Key Account Manager (f/m/d) - Full-time
- Vice President of Growing Operations
- Account Manager - United States
- Procurement Manager Blueberries
- International Fruit Trader
Impact of screen gaps above the central path
A Ventilation Jet system blows dry and cold air from the top compartment into the greenhouse to lower the greenhouse relative humidity (and temperature). By using a screen gap above the main path, the excess heat and humidity could escape. The efficacy of this system was investigated at a commercial greenhouse; the air flow through the VJ and through the screen gap as well as the horizontal temperature profile were measured in spring 2017.
The outcome was that less than 3% of the incoming air leaves the greenhouse through the screen gap above the central path; the vast majority of the air (> 97%) passes through the screens to the top compartment. It can be therefore concluded that the small gaps above the central path should not be applied in the specific greenhouse. Horizontal temperature difference (2.0 °C - 2.7 °C per 100 m) was recorded when both screens and supplementary lights were used. Closing the gap above the main path and replacing it with more and evenly spaced gaps with controllable size can probably homogenize the temperature distribution. This horizontal temperature difference did not occur when the supplementary lights were switched off.
The described study was part of “Kas als Energiebron” program, it took place at Gardener’s Pride greenhouse in Beetgum, NL and it was funded and performed in cooperation with LTO Glaskracht Nederland and the Dutch Ministry of Economic Affairs.
Source: Wageningen University & Research
Receive the daily newsletter in your email for free | Click here
Other news in this sector:
- 2023-11-29 How to use AI to support your floral business
- 2023-11-28 Fraunhofer FEP uses Microdisplays to monitor ornamental plants
- 2023-11-23 Effects of growth retardants on dwarfing performance of ornamental flowering plants
- 2023-11-22 How AI-led climate modelling could save millions of dollars
- 2023-11-22 Bosman Van Zaal now official dealer of Elpress
- 2023-11-22 From fragmented IT systems to Agriware 365
- 2023-11-21 What flowers can you grow in a hydroponic system?
- 2023-11-21 Google's GraphCast can predict weather with 'unprecedented accuracy'
- 2023-11-21 $17M for dynamic greenhouse lighting
- 2023-11-21 New cover film integrates fluorescent technology
- 2023-11-17 Enhanced Screen Calculations in software update Hortinergy
- 2023-11-17 100 years of phytopathology at Wageningen: a century of research into plant diseases
- 2023-11-17 Why do crops grow better with more light?
- 2023-11-16 No feed-in costs, and profit with energy optimization
- 2023-11-16 "High venting requirements make gaseous CO2 enrichment unfeasible"
- 2023-11-16 How to select the right mesh system for a greenhouse?